Little Eaton Water Treatment Works (WTW)
Little Eaton Water Treatment Works (WTW) is located North West of Derby just off the A38.
The Water Treatment Works is supplying safe, clean drinking water to the growing community of Northwest Derby, originally designed for a maximum water output of 85mld. The operational efficiency had been severely compromised due to a number of factors and the equipment was in need of a major overhaul.
The works process consists of the following operations;
- Raw water Inlet pumping station.
- Lamella clarifiers
- Rapid Gravity Filters
- Granular Activated Carbon
- Disinfection Contact Tank
- High Lift Pump Station into Supply.
The need for change
The fragile Lamella plates were life expired and required extensive labour to maintain efficient water production output.
The clarifier tanks in which the plates were housed required draining every two weeks just to keep the plates clear of sludge build up. This was a maintenance-intensive task that was further complicated by a troublesome scraper system, which was prone to mechanical failure that resulted in scraper blades falling off. Diagnosing the problems required the isolation of equipment and removal of sludge build-up in order to make a thorough assessment.
Engineering a Solution
The team set to work refurbishing the two Lamella tanks using innovative design to provide the required quality and flow output. They considered ways to improve access to the equipment in order to facilitate future maintenance operations.
Hydro were commissioned to refurbish two of the existing Lamella tanks at Little Eaton WTW, using innovative design in deeper than normal lamella packs to achieve the required quality and flow output.
The design also looked at the access for any future cleaning down and maintenance requirements and positioning of a new control panel in an already very tight environment
It took a team of dedicated professionals to implement a solution, but it was anything but clear how the task would be accomplished or if they could deliver the solution by the completion date established by the Drinking Water Inspectorate.
With the collaborative efforts and dedication from the MWH Treatment, Hydro International and Severn Trent Water teams, this date was achieved three months ahead of time with the first tank gaining “plant in use” on 22nd December 2016.
The challenges started on day one, as the team sorted out the plethora of operational and functional problems at the 20-year-old facility.
For starters the new larger Lamella plates, the first of its kind in the UK and are larger than the traditional plates. A lot of time and collaborative working between all parties was necessary to ensure proper fit and function in the existing settlement tanks.
There was a need to understand the best way to secure removal of the old plant from the existing tanks. This was achieved by carrying out assessments in order to estimate the weight of the old units and how fragile the existing Lamella packs might be. Additional planning was required to establish how to deal with the significant amounts of heavily compressed sludge on the old Lamella packs and in the base of each tank.
Working in conjunction with two other major capital schemes (Sludge improvements and Rapid Gravity Filter refurbishment) greatly increased the need for good communication and careful clear planning. Good coordination was essential for the lifting operations to crane in and install the new and significantly larger build packs. The Build packs had been manufactured off site and delivered in-situ within the existing settlement tanks.
The teams needed to find a safe and secure way to access the existing, plastic lamella packs for removal whilst ensuring the prevention of hydraulic oils spills that could contaminate lamella tanks in event of hose leakages. It was essential to provide a stable lifting platform around critical services to position a 100 Ton crane to allow 16 pre-built 10m long Lamella packs weighing over 4 Tons to be lifted. Consideration was also given to of removal of side wall panels to prevent imploding of Lamella structure due to wind loads.
All these works were to be carried out whist causing minimum disruption to the existing water supply.
Whilst it was recognized that the first tank would pose some challenges due to nature of construction, MWH looked at providing safety wires stretched along the length of the lamella packs by which the operators could move around the area with a hitching process similar to high tree trekking.
Initial attempts at removing the old lamella packs proved cumbersome and long winded due to the packs breaking up and splitting so the MWH operators came up with a fabricated combination of straps and a steel lifting device which was easy to manhandle and set up and once implemented which saved approximately 60% on the removal time.
By utilizing the position of the crane during the removal the redundant equipment in the tank, it was possible to build the new Lamella packs offline in controlled assembly line conditions. This was in readiness to lift the plates into the tank, reducing overall project time and health and safety risk associated with spending time in the tank.
Leaving a lasting legacy
The site team have optimized the new system to prove that a single tank can operate at 60MLD and at present a combination of the 2 tanks can achieve an increased output of 120MLD.
The second tank was completed, and “plant in use” achieved, on 19th April 2016. The first tank has been drained and inspected after 6 months of operation and all found to be in good order.
By adopting a factory thinking approach and building off-site, the profiles of the plates were delivered to site prior to assembly in the tanks. The new plates were installed in 2 days; a task that would traditionally take around 6 weeks. By using this method the teams were able to reduce cost, time on site and eliminate risks. By isolating the one tank at a time MWH were able to maintain the existing water supply causing zero disruption to the people of North West Derby.
The new Lamella plates are heavier and longer than the previous plates making it easier for larger quantities of flock to settle enabling the plant to process larger volumes of water effectively. As a result of the works the plant will serve the community of North West Derby for many years to come and with the population of North West Derby anticipated growth the site is equipped to accommodate the growing population and the extra demand on the water supply by increasing the potential output from 90MLD to 120MLD per day.